EXAlR Cabinet Cooler Systems include a 5 micron automatic drain water and dirt filter. This filter is critical for protection of electronics from water in the compressed air line. If oil is present in the compressed air supply, the addition of a coalescing (oil removal) filter, such as EXAlR Model 9005, is recommended.
|Cabinet Cooler Systems:|
Systems for continuous operation
include a Cabinet Cooler, cold air
distribution kit and filter.
Systems with thermostat control
include a Cabinet Cooler, thermostat,
solenoid valve, cold air distribution
kit and filter.
Cold Air Distribution Kit:
The kit includes a length of flexible vinyl tubing used to direct the cold air for circulation, or to hot spots. Tubing connectors and adhesive backed clips to hold the tubing in place are provided.
Cold Air Distribution Kit includes tubing, adhesive clips and fittings.
For a continuous operating Cabinet Cooler, relative humidity inside the enclosure stabilizes at 45%. No moisture condenses inside the enclosure. (The enclosure must be sealed to prevent condensation.)
Inlet Air Temperature:
Cabinet Cooler Systems provide a 50°F (28°C) temperature drop from supply air temperature when the inlet pressure is 80 PSIG (5.5 BAR). Elevated inlet temperature will produce a corresponding rise in cold air temperature and reduction in cooling capacity. Low air pressures will also reduce the cooling capacity.
The Cabinet Cooler mounts to the enclosure through a drilled hole or electrical knockout. The NEMA 12 (IP54) Cabinet Coolers may be mounted on the top or side of the panel. Side Mount Kits are available. (Model 4909 - Small; Model 4910 - Large.) NEMA 4 and 4X (IP66) Cabinet Coolers may be mounted on the top of the panel or on the side of the panel if a Side Mount Kit is used (Model 4906 - Small; Model 4907 - Large). Click here to purchase a Side Mount Kit for your Cabinet Cooler.
Solenoid Valve and Thermostat:
Cabinet Cooler Systems with thermostat control include a solenoid valve and thermostat that limit the flow of compressed air to only when cooling is needed. The solenoid valve is rated 120V, 60Hz or 110V, 50Hz. It is UL Listed, CSA Certified.
The thermostat is factory
set at 95°F (35°C). It will normally
hold ±2°F (1°C) inside the cabinet. It is rated 24VAC-240VAC, 50/60Hz, 24VDC and is UL Recognized, CSA Certified.
Solenoid Valve (bottom) and Thermostat (top).
|Electronic Temperature Control:
EXAIR’s digital ETC™ (Electronic Temperature Control) provides precise temperature control for your electrical enclosure. It can accurately maintain a constant temperature that is slightly under the maximum rating of the electronics, permitting just enough cooling for the electronics without going so cold as to waste compressed air.
The LED readout of the ETC displays the internal temperature of the electrical enclosure (°F or °C) that is constantly being monitored by a quick response thermocouple. The control activates the solenoid valve (included) when the temperature setting is exceeded. The polycarbonate plastic enclosure of the ETC is suitable for NEMA 12, 4 and 4X environments. (Cabinet Cooler not included.)
Model 9238 - 120VAC, 50/60Hz
Model 9239 - 240VAC, 50/60Hz
Setting Temperature: Membrane push button control
Power Supply Current: 165mA
Sensor: Type J Thermocouple
NEMA 4X, IP66, UL508
Temperature Sampling Rate:
Max. Temp.: 158°F (70°C)
Solenoid Valve: 1/4 NPT